Fire alarm for powered doors
Facility name: Regional Medical Center Of San Jose
Location: SAN JOSE, CA
Project classification: Hospital – Renovation
Project type: Acute Care
Project number: 0838500026
Lesson Learned number: 187
Impact: Cost, Schedule
Cost impact: $8,500 Schedule impact: 7 days
Lesson Learned/Best Practice
On this project the fire alarm was designed prior to bid and the completed fire alarm shop drawings were part of the bid package and not created as a deferred submittal by the fire alarm subcontractor. We had numerous doors with auto operators, and the fire alarm shop drawings didn’t capture the code-required relay that triggers those powered doors to close when the alarm activated.
Suggested Actions for Future Projects
Ensure fire alarm design that is included in the Permit/OSHPD documents identifies rated openings and auto operators and include the required Fire Alarm Integration, relays, etc. If fire alarm design is a post Permit/OSHPD approval (like an OSHPD deferred approval), then note this requirement within the specification for integration with the project fire alarm system.
Fire Alarm, Doors, Operators