Facility name: UCF Lake Nona Medical Center
Location: TALLAHASSEE, FL
Project classification: Hospital – New
Project type: Acute Care
Project number: 2689500001
Lesson Learned number: 121
Impact: Cost, Scope
Cost impact: $25,000
Lesson Learned/Best Practice
AHCA requires that any OR space that does not have medical gas on the surgical boom must have the med gas outlets “convenient to the bed”. (within 6′) If the center of the bed does not fall within this 6′, a med gas pedestal must be added at the center of the room.
Suggested Actions for Future Projects
Any OR project in the state of Florida where a surgical boom is installed without med gas, special consideration should be given to incorporating a med gas pedestal.