Facility name: UCF Lake Nona Medical Center
Location: TALLAHASSEE, FL
Project classification: Hospital – New
Project type: Acute Care
Project number: 2689500001
Lesson Learned number: 126
Lesson Learned/Best Practice
AHCA requires that any piece of electrical equipment that is preassembled carry a UL listing or be field listed. Aiphones do not carry a UL listing and cannot be field listed without a Class “2” power supply. A Class II power supply is not permited.
Suggested Actions for Future Projects
Low voltage subcontractor should carry cost to swap out power supplies from Class II to Class 2 for any projects in Florida.